Quotes and Questions:
Steve@jsicoatings.com --- (936) 321-3333
We are Elite Distributors for Raychem / Tyco Electronics and Master Distributors for Covalence Heat Shrink Sleeves Call: 936/321-3333 Email: Stacey@jsicoatings.com or Steve@jsicoatings.com Visit our official site: www.heatshrinksleeves.com Pipeline Blog: blog.heatshrinksleeves.com
Friday, August 30, 2013
In Line Cold Splice for a #16 Cable
Question: I love using the GHFC. It is incredibly fast, easy and reliable. Do you have a GHFC size that will work with #16 cable?
Answer: Unfortunately, the #16 wire is just barely outside of the use range for the GHFC-1-90. The GHFC-1-90 is approved for use on a #14 cable (.0641" diameter) and a #16 cable has a diameter of .0508". This is obviously incredibly close with a difference of only 13 thousands of an inch, but still - it just can't be sanctioned. The simplest solution in a case like this would be to purchase some additional GelTek tape. Even a single wrap around the wire would get its diameter on par with the #14 (or greater) and the GHFC could then be used. One extra step, but now you can go back to using the simple and easy GHFC inline splice.